|Water Source Type||Borewell Water|
|RO Capacity||1000-2000 (Liter/hour)|
|Max Water Recovery Rate||55-60 %|
Scheme of Treatment:
- Raw water after oxidation is passed through Stainless steel Multigrade sand bed pressure filter to remove suspended impurities and precipitate of iron and manganese.
Activated Carbon Filter:
- Water stream coming from coarse filter is passed through Stainless steel activated carbon filter which ensures odour, colour free filtered water also free from residual chlorine.
- To maintain desired level of minerals / TDS in final product, major part of pretreated water shall be desalinated by RO with molecular rejection of dissolved solids. In molecular rejection, the hardness forming ions (Ca & Mg) may get deposited over membrane surface as a scale.
Pretreatment for Reverse Osmosis Stream:
- A food grade anti scalent dozing is done to soften the water
Fine Filtration by Multi Micron Cartridges Filter:
- By above process of pretreatment, water becomes free from undissolved solids, iron, manganese and organic matters & filtered water upto 20 microns by particle filtration. Keeping in view of porosity below 0.0005 microns and other characteristics of RO membranes, the make have specified that ideal SDI of RO feed water should be below 3 which is possible if water is properly filtered by micron cartridges of rating below 5 microns.
- Therefore we provided multi micron cartridges in stainless steel housing rating 5 microns to achieve ideal SDI level. Since in blending stream purification everything has to be removed except minerals
Desalination by Reverse Osmosis Unit:
- Reverse Osmosis is based on the technology which removes total dissolved solids by their molecular rejection. In the process pretreated water is pumped to membrane and feed pressure is increased above osmotic pressure. As a result pure water migrates from the concentrate to produce perfectly sterilized desalinated water. The system is designed based on raw water analysis treated water quality & recovery.
- We offer RO block fully automatic with synchronized logic control & instruments for on-line measurement of parameters to ensure safe and efficient working as well as treated water quality control revive the unit, but it never produce the specified output as well as quality of treated water also Detroit after cleaning.